|Place of Origin:
|ASME, ISO9001, EN
|Minimum Order Quantity:
|2,000 - 5,000 USD per pc
|Sea worthy Packing for Exporting with Iron Frame
|Within 90 Days after getting the down payment or L/C
|T/T, L/C at sight
|About 1,000 tons per month
|Boiler Maintaince,Boiler Pipe,Heating Element
|Industrial,Power Station,Thermal Power Plant/station Boiler
|Horizontal And Vertical
Wear Resistant Shield Superheater And Reheater,
Stainless steel Biomass Superheater And Reheater,
Customized Biomass Superheater And Reheater
Wear-Resistant Shield Carbon Steel Superheater And Reheater Waste To Energy Power Plant
Superheater and Reheater
Anti-wear shiemainly used in the boiler superheater, reheater, economizer, water wall pipe heating surface pipe windward side, and induced draft fan will also be used (little amount), the main role is to protect the boiler pipe by the wind surface, reduce pipe wear, increase the service life of the heating surface pipe. General industry known as "anti-wear tile", "anti-wear cover plate". Anti-wear shield is a special boiler accessories, generally used in power plant boilers, small boilers are used less, some coal chemical industry will also be used.
Super heaters are the one of the most important boiler sapre parts that improves the thermal efficiency. High temperature steam boiler radiant super heater is usually applied in high pressure power plant boiler. Super heater coils are used in a boiler to generate saturated steam. The super heater coils are specially used in Boilers of Power plant. We manufacture Super heater coils in various grades of Alloy steel and in stain less steel tubes with or without support & Header as per customer's drawing.
Changes in boiler operating conditions, such as load level, fuel change, combustion condition change, etc., all have an impact on superheater outlet steam temperature, so in power station boilers there are means to adjust boiler outlet steam temperature to make it stable at the specified value.Commonly used means are:
(1) with water jet or surface type temperature reducer directly adjust the steam temperature;
(2) with the swing burner to change the temperature of the furnace outlet smoke;
(3) with smoke recirculation adjustment superheater heat absorption.When the boiler load increases, the temperature rise value of the inlet and outlet steam of the flow superheater increases, while the temperature rise value of the radiant superheater decreases.
Superheater tube wall in the boiler pressure parts under the highest temperature, so must use high quality low carbon steel and various chromium molybdenum alloy steel, in the highest temperature part sometimes also use austenitic chromium nickel stainless steel. In boiler operation, if the temperature of the pipeline exceeds the allowable temperature limit of the material's durable strength, fatigue strength or surface oxidation, the pipeline burst will occur.
The outer diameter of the pipe is generally 30 ~ 60 mm.The most common type of superheater is the serpentine tube.It has a relatively dense tube set, arranged in the flue gas temperature of 450 ~ 1000℃, by the transverse and longitudinal erosion of flue gas.The flue gas mainly transfers heat to the pipe by convection, and some radiation absorbs heat.Screen type superheater consists of a plurality of tube screen, arranged in the upper part of the furnace or the outlet, belongs to the radiation or semi-radiation superheater.The former absorbs the radiant heat of the furnace flame, while the latter absorbs part of the convective heat.In the power station boiler above 10 mpa, generally both screen type and serpentine tube type superheater are used to increase heat absorption.The wall superheater applied to the inner wall of the furnace is the radiant superheater, which is seldom used.Wall type superheater is used in large capacity power station boiler to form the wall of the furnace roof and convection flue, and the insulation material is applied outside to form the light furnace wall.
|1.Firm structural support
|1. Flow blockage by condensed steam 2. Needs a slow restart to purge the water that accumulates in the bottom.
|supported from above
|1.Proper drainage of the condensed steam
|1. Lack the structural rigidity, especially in high speed gas flow
|Supported from below
1. Proper drainage
2. Good structural rigidity.
|1. They do not view the flam directly so they are mainly from the convective type
|Usually supported in the vertical gas ducts parallel to the main furnace.
• Principle of superheater is similar to steam generating tubes of boiler.
• The hot gases at high temperature sweep over superheater tubes and raise the temperature of steam which magnitude depends upon exit gas temperature leaving the superheater and gas velocity.
Use for heating saturated steam, steam temperature could be up to 900 degree C.
Superheater Capacity Upgrades to Increase Power Generation
Send us required technical data, such as steam capacity, presure, required temperature etc. We will design accordingly.
Contact Person: Miss. Sandy Chen
Fax: 86- 512-58774453
Address: Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China
Factory Address:Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China