|Place of Origin:||Jiangsu, China|
|Certification:||ISO, ASME, EN|
|Model Number:||Superheater Coil|
|Minimum Order Quantity:||20 Tons|
|Packaging Details:||Steel Frame|
|Payment Terms:||L/C, T/T|
|Product Name:||Boiler Superheater Pendant||Material:||SA213-T22 And SA240-TP310S|
|Keywords:||Primary/Secondary Super Heater Pendant||Tube Bending Technique:||Cold/Hot Bending|
ASME Boiler Superheater,
industrial Boiler Superheater,
ASME Boiler Superheater Pendant
ASME Boiler Superheater Pendants Of With 360° Shields For Waster Incinerator
A superheater is a component that heats saturated steam in an industrial boiler, turning it into superheated steam. Our superheater guarantees that the superheated steam temperature will fluctuate to within an allowable range (normally varies from 540℃ to 550℃) when the boiler is over loaded.
Superheaters and reheaters are important parts for the heating surfaces, used to increase steam temperature, aiming to improve steam enthalpy and further to increase the thermal circulation efficiency for power station.
The function of superheater is to heat saturated steam into superheated steam of some temperature. The superheater is divided into rear platen superheater, final superheater, vertical low temperature superheater, horizontal low temperature superheater, etc. according to its layout and heat transfer mode.
According to the installation mode in the boiler, the serpentine tube panel can be generally divided into two types: vertical suspension type and horizontal suspension type. The vertical suspended serpentine tube panel is generally a single-layer structure, which is mainly used in the high-temperature section of the superheater and reheater. The end of the tube panel is directly connected with the pipe joint of the header, suspended and arranged in the longitudinal direction of the header, and penetrated the ceiling of the furnace chamber, and sealed with it through the accessories on the tube panel; The horizontal suspended serpentine tube panel, most of which are of double-layer structure, is fixed and suspended by water-cooled hanging tube in the middle, and is generally used in the low temperature section of superheater and reheater and the serpentine tube of economizer.
There are different types of super heaters with advantages and disadvantages as below:
|Pendant-type||1.Firm structural support||1. Flow blockage by condensed steam 2. Needs slow restart to purge the water that accumulates in the bottom.||supported from above|
|Inverted-type||1.Proper drainage of the condensed steam||1. Lack the structural rigidity, especially in high speed gas flow||Supported from below|
1. Proper drainage
2. Good structural rigidity.
|1. They do not view the flam directly so they are mainly from the convective type||Usually supported in the vertical gas ducts parallel to the main furnace.|
For over 30 years, Hua Dong Boiler has been consistently innovating and improving our boiler superheaters and reheaters. The improvements in bending, welding and design ensure our products meet both European and American standards, ensuring a reliable performance.
The materials and tube diameter range of our super heater and reheater are indicated as below:
Materials for superheater & reheater
nickel and special alloys
Tube diameter range of our superheater & reheater
Contact Person: Wendy
Address: Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China
Factory Address:Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China