|Place of Origin:||China,Zhangjiagang|
|Brand Name:||HD Boiler|
|Certification:||ISO9001 , SGS , ASME "S" "U", Grade A|
|Model Number:||Secondary Superheater|
|Minimum Order Quantity:||1Set|
|Packaging Details:||Seaworthy Packing|
|Delivery Time:||35 Days|
|Payment Terms:||L/C, T/T, D/P|
|Supply Ability:||1500 Tons / Month|
|Range Of Applications:||US Power Plant||Specification:||Customized|
|Surface Treatment:||Anti Corrossion||Certification:||ISO, ASME,EN,TUV|
reheater in power plant
Boiler Superheater And Reheater Coils For Power Plant TP321 High Corrosion ASME
Superheater&Reheater, Custom Component For Boiler
A superheater is a component that heats saturated steam in an industrial boiler, turning it into superheated steam. Our superheater guarantees that the superheated steam temperature will fluctuate to within an allowable range (normally varies from 540°C to 500°C)when the boiler is over loaded.
Super heater types:
1. Radiant super heater: it is the earliest type of super heater and it is located above or behind banks of water tubes to protection them from direct flam or fire.
Parameters that increases the convection
a. Increasing the fuel-and air flow (combustion gas flow)
b. Increasing the mass flow rate of the steam
Radiation is mainly dependent on the flam temperature. as the steam flow rate increases the exit temperature become lower.
Radiant super heater
They are placed exposed to the heat source whcih requires the improvement of metal temperatures.
Radiant and convetive super heaters and reheaters are used for high temperature steam.
The accessory of high temperature radiant steam super heater in boiler
It is made up of snake-like tubes (carbon steel, alloy steel or heat-resistant steel, etc.) and collection boxes and other supporting material. Tubes generally have φ32, φ38, φ42 or other types of specifications, according to user's needs separately.
They are the sane as the super heaters but as their exit temperature is a little bit less than super heaters and their pressure is 20% -25% less than the super heater, they can stand less quality material alloys.
Steam super heater is consisted of dense tube coils and is placed in the flue under the tempearture 450ºC-1000ºC.
For power plant boiler capacity over 10Mpa, platen and coiled superheater are usually adopted.
What are the differences of Superheater And Reheater?
|Pendant-type||1.Firm structural support||1. Flow blockage by condensed steam 2. Needs slow restart to purge the water that accumulates in the bottom.||supported from above|
|Inverted-type||1.Proper drainage of the condensed steam||1. Lack the structural rigidity, especially in high speed gas flow||Supported from below|
1. Proper drainage
2. Good structural rigidity.
|1. They do not view the flam directly so they are mainly from the convective type||Usually supported in the vertical gas ducts parallel to the main furnace.
|structure||horizontal or vertical|
|material||carbon steel, alloy steel|
|tubes||φ32, 38, 42, etc.|
Send us required technical data, such as steam capacity, presure, required temperature etc. We will design accordingly.
Hua Dong Boiler has become a major qualified supplier of domestic and foreign boiler manufacturers and energy companies, including American Covanta Energy Company, AMEC Foster Wheeler Company, ALSTOM, Oriental Boiler Limited by Share Ltd., Harbin electric LLC, Wuxi Hua Guang Boiler Co., Ltd., Hangzhou Boiler Group Co., Ltd.
Contact Person: Miss. Sandy Chen
Fax: 86- 512-58774453
Address: Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China
Factory Address:Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China