|Place of Origin:||China|
|Certification:||ASME, EN, ISO9001, SGS|
|Model Number:||Boiler Economizer|
|Minimum Order Quantity:||1 set|
|Packaging Details:||Seaworthy packing|
|Delivery Time:||30~50 days|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||500 tons per month|
|Type:||Economizer||Application:||Power Plant Boiler|
|Material:||Carbon Steel Or Stainless Steel||Product:||Boiler Economizer|
Carbon Steel Or Stainless Steel Economizer In Power Plant , Economizer Tubes
Economizer tube is an important part of boiler, which is mainly made of seamless steel tube by bending or folding.
Cast iron economizer consists of a series of horizontal cast iron pipes connected to each other with cast iron elbows and flanged ends.
The tubular economizer consists of a series of parallel serpentine tubes, which are made of seamless steel pipes with an outer diameter of 25 ~ 42 mm, and the pipes are usually arranged in a staggered arrangement.
Boiler economizer is kind of heat exchanger to heat the feed water using the flue gas heat. The flue gas coming from the tube outside is up and down cross-flow scrubbing the tube bundle, passing the heat to the tube wall. The water is flowing from bottom to top, and absorts the heat from the tube wall, and its temperature is getting high. This way not only can countercurrent heat transfer to save metal consumption, but also is good for water/steam to flow and exhaust as well as decreasing corrusion. One more, this way works well for dust cleaning.
1.Fuel saving: the economizers are placed at the rear part of boilers. This way can decrease the smoke and gas temperatures, thus to save fuels.
2.Improve the working conditions of steam drums: due to economizers, the feed water temperature is increased when entering the steam drum. It reduces the temperature difference between the feed water and steam drum wall as well as steam drum thermal stress, so that it improve the working conditions of steam drums and increase the service life.
3.Reduce the boiler manufacturing cost: for the feed water is heated in the boiler economizers. The use of low temperature spare parts as boiler economizers to replace some of high-priced high temperature water wall panels reduces the cost to manufacture boilers.
|Material||Alloy steel, Carbon steel, SA210C ,SA213T22, etc.|
|Material standard||ASTM, EN or ISO etc.|
Min: 10 ton
|Smelting Process:||EF+LF + VD|
|Process||Material→Ingot → Hot/Cold-Rolling→ Heat treatment (Normalizing+ tempering) → Inspection →rough machining→UT →2nd Heat treatment →finishing machining →Inspection|
|UT standard||ASTM A388 or EN10228, etc|
There are three stages from the feed water in the boiler heated into superheated steam:feed water preheating, evaporation, and superheating. The three stages are finished on three different heating surfaces. The boiler steam and water circuit are composed of the three different heating surfaces as well as their connecting pipes. Boiler economizers are one of them, and it is right the equipment to preheat the feed water. Thus, it is the heating surface with the lowest temperature for boiler working fluid in the boiler steam and water circuit. The working fluid passing through this equipment is monophasic water(non-boiling economizer).
The products of our company have been widely used in major power plants of various provinces and cities in China, bringing stable and significant economic and social benefits to cooperated power plants. At the same time, we attach great importance to product development and strive to improve product quality. Through the cooperation with a number of domestic and foreign companies, we constantly explore the international market.