|Place of Origin:||ZhangJiagang , Jiangsu , China|
|Brand Name:||HD BOILER|
|Certification:||ISO9001 , SGS , ASME , EN , TUV|
|Model Number:||Spiral Fin Tube|
|Minimum Order Quantity:||1 Set / Sets 10tons|
|Packaging Details:||Iron Frame Packing|
|Delivery Time:||50-100 days|
|Payment Terms:||L/C, , T/T, , Western Union|
|Supply Ability:||500 Tons Per Month|
|Application:||Power Plant Boiler||Pressure:||High Pressure|
|Range Of Applications:||Power Station , Industrial||Specification:||Customized|
|Surface Treat:||Painted||Function:||Heat Exchanger|
|Material:||Carbon Steel / Stainless Steel|
Power Plant Boiler Spare Parts Superheater And Reheater Of Carbon Steel
In modern boilers, the heat absorption consumption of the superheaters and reheaters is over half of total heat absorption for the working fluid, thus the heating surfaces of superheaters and reheaters account for a large proportion in total heating surfaces of boilers, and they must be placed in the areas where smoke temperature is higher, the working conditions are the worst among all the heating surfaces.Tube wall temperature of the heating surfaces is close to the max. allowable temperature of steel, so the reasonable arrangement and design of superheaters and reheaters matter so much for economy and reliability to the while boiler. When it comes to their design, on the basis of assurance of safety and reliability of superheater and reheater, it is very necessary to save metal consumption at the best, especially to save usage of alloy steel.
For boilers in large power stations, superheaters and reheaters are necessary parts, to a large extend, they have influnced the safety and economy of boilers. Superheaters are the heating surfaces which heat the main steam from the surnatured temperature to the rated superheated temperature, and the reheaters are the heating surfaces which heat the exaust from the steam turbine high pressure cylinder to a certain temperature.When running conditions like boiler loads, coal types change, it is to adjust them to make sure the outlet temperature at the rated level of -10-+5 degrees.
For large boilers in power stations, superheaters and reheaters account for a big proportion in the total heating surfaces, they are to be arranged in the areas where smoke is with higher temperature. To improve the efficiency of thermal circulation in power stations, it is needed to improve the original parameters f steam gradually, the increase of steam pressure requires the corresponding increase of temperature for superheated steam, or the humidity of large stage exhaust of steam turbine will be too high, which will influence its safety. Thus, the steam flowing through superheaters and reheaters are high temperature steam, their heat transfer performance is quite bad, which determines that tube wall temperatures of superheaters and reheaters are high.
Functions and characteristics of superheaters and reheaters
functions of superheaters and reheaters:
Superheaters and reheaters are important parts for the heating surfaces, used to increase steam temperature, aiming to improve steam enthalpy and further to increase the thermal circulation efficiency for power station.
Superheaters work to heat surnatured steam to superheated steam with a certain tempetature. When boiler loads or other working conditions change, it is necessary to make sure superheated steam temperature to be normal, and within allowable range of temperature variation.
From the thermal circulation in power station, the original parameters of pressure and temperature is higher, the thermal efficiency of circulation is better, or the steam humidity of the steam turbine rear is too high, influencing its safety. While the superheaer steam temperature is limited by metal materials, at present, due to limitation of metal materials, superheated temperature for most power station boilers are still within the range of 540-555 dgrees, and to avoid the steam humidity of blade of steam turbine rear too big, thus middle reheating system is applied.
Functions of reheaters are to heat exhaust of steam turbine high pressure cylinder to the reheated temperature which is close or equal to superheated temperature, and then send them to middle pressure cylinder and low pressure to expand and work to increase the dryness of blace of steam turbine rear. Usually, the pressure of reheated steam is one fifth of that of superheated steam. Application of reheating system can increase the thermal efficiency for power stations by 4-5%.
So far in our country, units with capacity over 125mw all apply one time middle reheating system. Double reheating can increase again the thermal efficiency of circulation by 2%, but the system is very complicated, it is not applied for national units, but it is common for large boilers overseas.
HD Boiler established in 1985, Zhangjiagang Hua Dong Boiler Co., Ltd. (trading as HD Boiler), is a professional industrial manufacturer, producing utility boiler,industrial boiler,HRSG boiler and all kinds of boiler parts, such as waterwall panels, economizers, air preheaters, superheaters, headers, spiral fin tubes, H-fin tubes, heat pipes etc. HD Boiler is located in Dong Lai Industrial Park, east suburb of Zhang Jia Gang City. The plant’s location is around 150km Expressway to Shanghai Port or 60km State Road to Suzhou or Wuxi, with transportation extending in all directions conveniently and quickly.