|Place of Origin:||China|
|Brand Name:||HD BOILER|
|Certification:||ISO9001 , SGS , TUV , ASME , EN|
|Model Number:||Superheater and Reheater|
|Minimum Order Quantity:||1 set / 10tons|
|Packaging Details:||Seaworthy packing|
|Delivery Time:||50 ~ 100 Days|
|Payment Terms:||L/C, T/T, Western Union|
|Supply Ability:||1500 Tons / Month|
|Material:||Carbon Steel||Treatment:||Electrical Furnance|
|Hydraulic Test:||Accept||Tube Thickness:||Applicable|
superheater in boiler
Carbon Steel Superheater Coils Processing Hign Efficeint Heat Exchanger
|1||The efficiency of the steam cycle is improved by higher steam pressure and temperature as well as reheating.|
|2||Both superheating and reheating of steam have to be as high as possible. At a steam pressure of 120 bar and higher, the cycle efficiency improves by —1% for every 20°C rise in superheat.|
|3||Therefore, high superheats are desired for each band of pressure consistent with the metallurgy of the turbine.|
|In a subcritical boiler, the SH is between the main-steam header and the steam drum and consists of|
|• Saturated tubes that transport steam from the drum to the SH inlet header (when the SH tubes are not directly connected to the drum)|
• Superheater banks with their respective inlet and outlet headers
|• Attemperator station for STC|
|• Main-steam header with all fittings and terminating with the main-steam stop valve (MSSV)|
|Steam from the steam drum flows toward the main-steam header, and there should be no valve between the two to ensure flow in SH tubes under all conditions to prevent overheating and failure.|
Reheating of steam involves withdrawal of partly expanded steam (at the end of the high — pressure cylinder of the turbine), taking it back to the boiler in cold reheat pipes, heating to the same or higher temperature as the superheated steam, and returning to the turbine in hot reheat pipes. In terms of hardware, an RH system comprises
|• Cold reheat pipe from turbine to boiler|
|• Safety valves on the cold reheat pipe|
|• Emergency spray-water attemperator system on a cold reheat pipe or interconnecting pipe|
|• Reheater bank complete with inlet and outlet headers|
• Hot reheat pipe from boiler to turbine
Immerse the serpentine tube in a liquid container.When the inside of the snake is liquid.In order to constantly fill the whole pipe, the liquid should be fed from the lower end of the pipe to the upper end of the pipe.When steam is introduced into the snake tube, in order to avoid water hammer and blockage due to the accumulation of cold liquid in the tube, steam should enter from the top and condensate is discharged from the bottom.
The structure of submerged coil heat exchanger can be divided into two types: undetachable and detachable.In the selection, should be based on the cleanliness of the medium and corrosion.Packing height and material used.The choice of gasket materials can be determined by the use of pressure, temperature and the nature of the medium in the equipment.
Submerged coil heat exchanger, usually used for cooling, condensing or heating, cooling and evaporation of medium outside the tube.
Its advantages are simple structure, low cost and convenient operation and management.In addition, it can withstand high pressure in the coil. In addition, it is often used as the heat transfer component in the reactor with small heat transfer area.
Disadvantages: usually, the medium velocity in the container is very low, so the heat transfer coefficient outside the pipe is small.In addition, the overflow degree of all places in the container is roughly similar, so the average temperature difference is not large, so the heat transfer effect is poor.The equipment was bulky.Not suitable for use as a heat exchanger with large heat exchange area.
The material of superheater&reheater is steel pipe,copper pipe,other nonferrous metal,ceremic pipe,graphite pipe and so on.
Contact Person: becky
Address: Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China
Factory Address:Address: N0.1, Dongli Road, Donglai, Zhangjiagang City, Jiangsu Province, China